47' Cheoy Lee 1986 Efficient MY
4-MarineAir AC units
50 AMP service
Cape May, NJ and Georgetown, MD boating areas.
Steve: We installed the pump relay box you sent successfully (Marine Air 6PRP pump relay box). Now this mechanic originally wired the raw water pump motor incorrectly which we assumed knocked out (fuses kept blowing) the pump relay box. Now we have the new pump relay box installed that you sent us. The water flows through the raw water outlet in the hull successfully. The new motor for the raw water pump is running.
BUT, none of the 5 AC's are delivering cold air. Average temps were in the 80's while at the boats survey the average temps were approx. 52-58 degrees. (one year ago)
One AC unit seems to be cycling off and on every few minutes. The other AC's run but don't deliver any cold air.
So far we have installed a new raw water pump motor (Old motor wouldn't turn off until i thre the circuit breaker, then wouldn't turn on afterwards) and new pump relay box that's wasn't voltage sensitive (Marine Air 6PRP pump relay box).
What would you recommend at this stage?
Cape May, NJ
I'm glad your relay is working, but I think at this time I'd try to get a "Qualified" Marine A/C Tech out to take a look...
With 5 units not working...You with no experience...Me with no pressure readings or even knowing if compressors are running, what they are shutting off on, etc....
We might be here for your whole season back & forth...learning....
A qualified guy could get some baseline of whats happening in a matter of no more than an hour...Then you'll know where you stand.
My best advise ?....I wouldn't try to run these things until you do...You can do costly damage by doing so, and it seems they were operating well during survey...
You can find a dealer in your area thru this link ** you don't have permission to see this link ** by calling Marine Air at 1 800 542 2477.
Did what you suggested getting an marine AC tech on board for trouble shooting. Poor water flow and lack of freon were the issues. Tech back flushed the system, cleaning out the water flow paths. Now the discharge out the hull reminds me of a fire hydrant.
He charged the system with R-2.
Now taking steps to keep the water flowing with bromine and copper wiring. Going to put the copper wire coil into the water pump because theres a nice basket filter verses the thru-hole since they are close together. Will video record the discharge out the hull and take tempertures of all 5 AC units for a history. Any comments would be appreciated.
Thanks again for your valuable input.
Glad you are up & running
I use copper tubing in the strainer basket (more surface area than wire)
Just go to Home Depot buy a 4' length, and cheap tubing cutter...Cut the tubing to the height of the basket itself and put in 3-4 lengths.
I might also be concerned about where that freon went...These systems should not leak like a car with rubber hoses & compressor shaft seals.
They also don't like running low on freon so monitor them for loss of cooling...If they seem to not cool as well...Shut them off and get it checked again...Running low on freon kills compressors fairly quickly.
Thoughts about freon ?
No Hocus Pocus, It does not go bad, and No such thing as Freon Monsters that eat it up...
If it disappears...There is a leak.
Thats not to say that a system may not have been charged incorrectly previously...As I said...If you notice a drop in performance...Get it checked again...
If it's low again...There is a leak that needs to be located & repaired.
Freon was the question and thanks for the input. Seems opinions run wild.
Now Steve, is there a do it your-selfer chamethod to check for leaks. My girlfriend just said take a bottle of water and dishwasher liguid and spray on hoses and fittings and see if there's bubbles.
Jim Hughes enjoying very cool AC for now!
Most Users Ever Online: 95
Currently Browsing this Page:
Mr. Dee: 17
Ultimate Indulgence: 15
Ed D: 10
Guest Posters: 143
Newest Members:Jdm, jennysmith, Tom, Boaterbob, cuongquoc
Moderators: Steve Pooler: 1127
Administrators: Steve Pooler: 1127, Scott Pooler: 13